All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
ICS-CERT is aware of a public report of improper access control vulnerability affecting 3S CoDeSys. CoDeSys is a third party product used on programmable logic controllers and engineering workstations. According to this report, an attacker can upload unauthenticated configuration changes to the PLC which may include arbitrary code. This report was released by Reid Wightman, Digital Bond, without coordination with either the vendor or ICS-CERT.
ICS-CERT has notified the affected vendor of the report and has asked the vendor to confirm the vulnerability and identify mitigations. ICS-CERT is issuing this alert to provide early notice of the report and identify baseline mitigations for reducing risks to these and other cybersecurity attacks.
--------- Begin Update A Part 1 of 2 --------
The researchers have publicly released two tools containing exploit code for these vulnerabilities. The first tool can be used by an attacker to obtain a shell on the PLC. The second tool can be used by an attacker to transfer arbitrary files to and from the PLC.
The report included vulnerability details for the following vulnerabilities:
|Improper Access Control||Yes||Loss of integrity, confidentiality, availability|
|Directory Traversal||Yes||Loss of integrity, confidentiality|
Please report any issues affecting control systems in critical infrastructure environments to ICS-CERT.
--------- End Update A Part 1 of 2 ---------
ICS-CERT released the follow-up advisory ICSA-13-011-01 3S CoDeSys Vulnerabilities to the ICS-CERT Web site on January 11, 2013.
--------- Begin Update A Part 2 of 2 --------
3S has a Web site where asset owners can look up devices that uses CoDeSys. http://www.3s-software.com/index.shtml?codesys_dev_dir.
--------- End Update A Part 2 of 2 ---------
ICS-CERT is currently coordinating with the vendor and security researcher to identify useful mitigations.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices. Control system devices should not directly face the Internet.a
- Locate control system networks and devices behind firewalls, and isolate them from the business network.
- If remote access is required, employ secure methods such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a recommended practices section for control systems on the ICS-CERT Web site. Several recommended practices are available for reading or download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Organizations that observe any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. ICS-CERT ALERT, http://ics-cert.us-cert.gov/alerts/ICS-ALERT-10-301-01, website last accessed April 05, 2012.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.