All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
ICS-CERT is aware of a public report of multiple vulnerabilities affecting the WAGO IPC 758-870, which is an embedded Linux programmable logic controller (PLC). According to this report, an attacker could exploit these vulnerabilities to gain unauthorized access or to make unauthenticated configuration changes, which may include arbitrary code. The “Improper Access Control” vulnerability is the same vulnerability identified in ICS-ALERT-12-097-02—3S Software CoDeSys Improper Access Control.
ICS-CERT has notified the affected vendor of the report and has asked the vendor to confirm the vulnerability and identify mitigations. ICS-CERT is issuing this alert to provide early notice of the report and identify baseline mitigations for reducing risks to these and other cybersecurity attacks. This report was released by Reid Wightman, Digital Bond, without coordination with either the vendor or ICS-CERT.
The report included vulnerability details for the following vulnerabilities:
|Use of Hard-coded Password||Remote||Loss of integrity|
|Improper Access Control||Remote||Loss of integrity, possible arbitrary code execution|
Please report any issues affecting control systems in critical infrastructure environments to ICS-CERT.
ICS-CERT released a follow-up advisory, ICSA-12-249-02 - WAGO IO 758 Default Linux Credentials, to the ICS-CERT web page on September 04, 2012.
ICS-CERT is currently coordinating with the vendor and security researcher to identify mitigations.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices. Control system devices should not directly face the Internet.a
- Locate control system networks and devices behind firewalls, and isolate them from the business network.
- If remote access is required, employ secure methods such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a recommended practices section for control systems on the US-CERT website. Several recommended practices are available for reading or download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Organizations that observe any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. ICS-CERT ALERT, http://ics-cert.us-cert.gov/alerts/ICS-ALERT-10-301-01, website last accessed April 5, 2012. c. Control System
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.