All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
ICS-CERT is aware of a report of vulnerabilities with proof-of-concept (PoC) exploit code affecting Schweitzer Engineering Laboratories’ SEL-2032 Communications Processor SCADA remote terminal unit (RTU). This report is based on research conducted by Dillon Beresford and was presented by the Project Basecamp team during the Digital Bond SCADA Security Scientific Symposium (S4) on January19, 2012. According to their findings, the RTU uses plaintext protocol for password authentication. In addition, the researchers were able to cause an intermittent crash to an unknown service through Telnet and Port 1024/TCP. Vulnerability details were released without prior coordination with either the vendor or ICS-CERT.
ICS-CERT has coordinated with Schweitzer Engineering Laboratories and has asked the vendor to confirm the vulnerability and identify mitigations. ICS-CERT is issuing this alert to provide preliminary notice of the reported vulnerable product and to begin identifying baseline mitigations that can reduce the risk of cybersecurity attacks that may exploit these vulnerabilities.
The report included details and PoC exploit code for the following vulnerabilities:
|Plaintext Authentication||Local||Potential unauthorized access to system|
|Termination of the software||Remote||Denial of service|
Please report any cyber issues affecting control systems to ICS-CERT.
ICS-CERT is currently coordinating with Schweitzer Engineering Laboratories and Dillon Beresford to identify useful mitigations.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices. Control system devices should not directly face the Internet.a
- Locate control system networks and devices behind firewalls, and isolate them from the business network.
- If remote access is required, employ secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a recommended practices section for control systems on the US-CERT website. Several recommended practices are available for reading or download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Organizations that observe any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. ICS-CERT ALERT, http://ics-cert.us-cert.gov/alerts/ICS-ALERT-10-301-01, website last accessed January 20, 2012.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.