All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
ICS-CERT is aware of a public report of four vulnerabilities with proof-of-concept (PoC) exploit code affecting the ARC Informatique PcVue HMI/SCADA Version 10.0 product. According to the report, these vulnerabilities are remotely exploitable by using an ActiveX component within a targeted machine. This report was released without coordination with either the vendor or ICS-CERT.
ICS-CERT has not yet verified the vulnerabilities or PoC code but has reached out to the affected vendor to notify, confirm, and identify mitigations. ICS-CERT is issuing this alert to provide early notice of the report and identify baseline mitigations for reducing these and other cybersecurity risks.
The report included vulnerability details and PoC exploit code for the following vulnerabilities:
|Control of a function pointer||Remote||Denial of Service / Possible Remote Code Execution|
|Arbitrary Memory Write||Remote||Potential to Write Memory|
|Directory Traversal||Remote||Possible File Corruption|
|Array Overflow||Remote||Denial of Service/Potential Remote Code Execution|
Please report any issues affecting control systems in critical infrastructure environments to ICS-CERT.
ICS-CERT released a follow-up advisory, ICSA-11-340-01 - ARC Informatique PcVue ActiveX Vulnerabilities, on December 06, 2011.
ICS-CERT is currently coordinating with the vendor to identify useful mitigations.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices. Control system devices should not directly face the Internet.a
- Locate control system networks and devices behind firewalls, and isolate them from the business network.
- If remote access is required, employ secure methods such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control System Security Program also provides a recommended practices section for control systems on the US-CERT website. Several recommended practices are available for reading or download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Organizations that observe any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. CS-CERT ALERT, http://ics-cert.us-cert.gov/alerts/ICS-ALERT-10-301-01, website last accessed September 28, 2011.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.