All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Matrikon, a subsidiary of Honeywell
- Equipment: OPC UA Tunneller
- Vulnerabilities: Heap-based Buffer Overflow, Out-of-bounds Read, Improper Check for Unusual or Exceptional Conditions, Uncontrolled Resource Consumption
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to disclose sensitive information, remotely execute arbitrary code, or crash the device.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
Honeywell reports the vulnerabilities affect the following Matrikon products:
- OPC UA Tunneller: All versions prior to 18.104.22.16833
3.2 VULNERABILITY OVERVIEW
The affected product is vulnerable to a heap-based buffer overflow, which may allow an attacker to manipulate memory with controlled values and remotely execute code.
The affected product is vulnerable to an out-of-bounds read, which may allow an attacker to obtain and disclose sensitive data information or cause the device to crash.
Some parsing functions in the affected product do not check the return value of malloc and the thread handling the message is forced to close, which may lead to a denial-of-service condition.
The affected product has uncontrolled resource consumption issues, which may allow an attacker to cause a denial-of-service condition.
- CRITICAL INFRASTRUCTURE SECTORS: Multiple Sectors
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Canada
Uri Katz of Claroty reported these vulnerabilities to CISA.
Honeywell recommends upgrading Matrikon OPC UA Tunneller to Version 22.214.171.12433
CISA recommends users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.