All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 10.0
- ATTENTION: Exploitable remotely
- Vendor: Schneider Electric
- Equipment: Easergy T300
- Vulnerability: Missing Authentication for Critical Function, Missing Authorization, Missing Encryption of Sensitive Data, Improper Restriction of Rendered UI Layers or Frames
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker to obtain unauthorized access to the internal product LAN, which could result in exposure of sensitive information, denial of service, and remote code execution when access to a resource from an attacker is not restricted or incorrectly restricted.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
Schneider Electric reports this vulnerability affects the following firmware versions of the Easergy T300 products:
- Easergy T300 with firmware Versions 2.7 and prior
3.2 VULNERABILITY OVERVIEW
The affected product is vulnerable to a missing authentication for critical function vulnerability, which may allow an attacker to expose information, cause a denial-of-service condition, and remotely execute arbitrary code.
The affected product is vulnerable to a missing authorization vulnerability, which may allow an attacker to gain access to sensitive information, cause a denial-of-service condition, and remotely execute arbitrary code when access control checks are not applied consistently.
The affected product is vulnerable to a missing encryption of sensitive data vulnerability, which may allow an attacker to read network traffic over HTTP protocol.
The affected product is vulnerable to a missing encryption of sensitive data vulnerability, which may allow an attacker to read network traffic over IEC60870-5-104 protocol.
The affected product is vulnerable due to an improper restriction of rendered UI layers or frames vulnerability, which may allow an attacker to trick a user into initiating an unintended action.
- CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities, Energy, Food and Agriculture, Government Facilities, Transportation Systems, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: France
Evgeniy Druzhinin and IIya Karpov of Rostelecom-Solar and an anonymous researcher reported these vulnerabilities to Schneider Electric.
Schneider Electric recommends users upgrade to v2.7.1, which is available from the Schneider Electric Customer Care Center. Alternatively, users may disable port forwarding in the product firewall.
Schneider Electric strongly recommends the following industry cybersecurity best practices:
- Locate control and safety system networks and remote devices behind firewalls and isolate them from the business network.
- Install physical controls so no unauthorized personnel can access industrial control and safety systems, components, peripheral equipment, and networks.
- Place all controllers in locked cabinets and never leave them in “Program” mode.
- Never connect programming software to any network other than the network for which the devices are intended.
- Scan all methods of mobile data exchange with the isolated network (e.g., CDs, USB drives, etc.) before use in the terminals or any node connected to these networks.
- Never allow mobile devices that have connected to any other network, besides the intended network, to connect to the safety or control networks without proper sanitation.
- Minimize network exposure for all control system devices and systems and ensure that they are not accessible from the Internet.
- When remote access is required, use secure methods, such as virtual private networks (VPNs). Recognize that VPNs may have vulnerabilities and should be updated to the most current version available. Also, understand that VPNs are only as secure as the connected devices.
For more information refer to the Schneider Electric Recommended Cybersecurity Best Practices document.
Refer to Schneider Electric’s security bulletin SEVD-2020-315-06 for specific mitigation details.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability. High skill level is needed to exploit.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.