All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 4,3
- ATTENTION: Exploitable from adjacent network/low skill level to exploit
- Vendor: Tridium
- Equipment: Niagara
- Vulnerability: Synchronous Access of Remote Resource without Timeout
2. RISK EVALUATION
Successful exploitation of this vulnerability could result in a denial-of-service condition.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Niagara are affected:
- Niagara: Versions 188.8.131.52, 184.108.40.206, 220.127.116.11, 18.104.22.168
- Niagara Enterprise Security: Versions 2.4.31, 2.4.45, 22.214.171.124
3.2 VULNERABILITY OVERVIEW
A timeout during a TLS handshake can result in the connection failing to terminate. This can result in a Niagara thread hanging and requires a manual restart to correct.
- CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities, Critical Manufacturing, Government Facilities, Information Technology
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: United States
Honeywell reported this vulnerability to CISA.
Tridium has released updates that mitigate this vulnerability and recommends users update to the versions identified below:
- Niagara 126.96.36.199
- Niagara Enterprise Security 188.8.131.52
Updates are available by contacting the sales support channel or by contacting the Tridium support team at firstname.lastname@example.org
All Tridium Niagara users for all supported platforms are encouraged to update their systems with these releases to mitigate risk. For further guidance, please contact a Tridium account manager or Customer Support.
In addition to updating to the latest version, Tridium recommends users with affected products take the following steps:
- Review and validate the list of authorized users who can authenticate to Niagara.
- Allow only trained and trusted persons to have physical access to the system, including devices with connection to the system though the Ethernet port.
- If remote connections to the network are required, consider using a VPN or other means to ensure secure remote connections into the network.
For more information please refer to Security Bulletin SB 2020-Tridium-2.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.