All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Siemens
- Equipment: LOGO! Web Server
- Vulnerability: Classic Buffer Overflow
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of LOGO! Web Server are affected:
- LOGO! 8 BM (incl. SIPLUS variants):
- Versions between 1.81.01 and 1.81.03
- Version 1.82.01
- Version 1.82.02
3.2 VULNERABILITY OVERVIEW
A buffer overflow vulnerability in the Web Server functionality of the device allows an unauthenticated attacker to send specially crafted HTTP requests, which may cause memory corruption and result in remote code execution.
- CRITICAL INFRASTRUCTURE SECTORS: Chemical, Energy, Food and Agriculture, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Alexander Perez-Palma and Dave McDaniel from Cisco Talos and Emanuel Almeida from Cisco Systems reported this vulnerability to Siemens.
Siemens recommends affected users update to the following versions:
LOGO! 8 BM (incl.SIPLUS varriants):
- Versions between 1.81.01 and 1.81.03: Update to v1.81.04
- Version 1.82.01: Update to v1.82.03
- Version 1.82.02: Update to v1.82.04
Siemens recommends applying defense-in-depth concepts, including the protection concept outlined in the system manual.
Siemens recommends following their general security recommendations. As a general security measure, Siemens strongly recommends protecting network access to devices with appropriate mechanisms. To operate the devices in a protected IT environment, Siemens recommends configuring the environment according to the Siemens operational guidelines for Industrial Security and following the recommendations in the product manuals.
For additional information, please refer to Siemens Security Advisory SSA-573753.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.