All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Inductive Automation
- Equipment: Ignition
- Vulnerabilities: Missing Authentication for Critical Function, Deserialization of Untrusted Data
2. UPDATE INFORMATION
This updated advisory is a follow-up to the original advisory titled ICSA-20-147-01 Inductive Automation Ignition (Update A) that was published June 2, 2020, on the ICS webpage on us-cert.gov.
3. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to obtain sensitive information and perform remote code execution with SYSTEM privileges.
4. TECHNICAL DETAILS
4.1 AFFECTED PRODUCTS
The following versions of Inductive Automation Ignition are affected:
- Inductive Automation Ignition 7 Gateway versions prior to 7.9.14
- Inductive Automation Ignition 8 Gateway versions prior to 8.0.10
4.2 VULNERABILITY OVERVIEW
The affected product lacks proper authentication required to query the server.
The affected product lacks proper validation of user-supplied data, which can result in deserialization of untrusted data.
The affected product is vulnerable to the handling of serialized data. The issue results from the lack of proper validation of user-supplied data, which can result in deserialization of untrusted data.
--------- Begin Update B Part 1 of 2 ---------
Sensitive information can be obtained through the handling of serialized data. The issue results from the lack of proper authentication required to query the server.
--------- End Update B Part 1 of 2 ---------
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing, Energy, Information Technology
- COUNTRIES/AREAS DEPLOYED: United States
- COMPANY HEADQUARTERS LOCATION: United States
Pedro Ribeiro, Radek Domanski, Chris Anastasio (muffin), and Steven Seeley (mr_me) working with Trend Micro’s Zero Day Initiative reported these vulnerabilities to CISA.
Inductive Automation recommends upgrading the Ignition software to v8.0.10
For those running v7.9.x, it is recommended to upgrade the Ignition software to v7.9.14
--------- Begin Update B Part 2 of 2 ---------
Please note CVE-2020-14479 does not have a fix in place. Induction Automation plans to correct this vulnerability in future product versions.
It is recommended to restrict interaction with the service to trusted machines. Only clients and servers with a legitimate procedural relationship should be permitted to communicate with the service. This can be done in various ways, most notably with firewall rules/allow listing.
For more information regarding software and patches, please refer to the specified version in Inductive Automation’s release notes.
--------- End Update B Part 2 of 2 ---------
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.