All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 8.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Eaton
- Equipment: Intelligent Power Manager
- Vulnerabilities: Improper Input Validation, Incorrect Privilege Assignment
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to perform command injection or code execution and allow non-administrator users to manipulate the system configurations.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Intelligent Power Manager, a software monitoring and management platform, are affected:
- Intelligent Power Manager v1.67 and prior
3.2 VULNERABILITY OVERVIEW
The affected product may not validate import configuration file names properly, which could allow an attacker to perform command injection or code execution.
The affected product may allow non-administrator users to upload the system configuration files by sending specially crafted requests, which could allow non-administrator users to manipulate the system configurations.
- CRITICAL INFRASTRUCTURE SECTORS: Energy
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Ireland
Sivathmican Sivakumaran of Trend Micro’s Zero Day Initiative reported these vulnerabilities to CISA.
Eaton has released Intelligent Power Manager v1.68 to address the reported vulnerabilities.
To prevent the exploitation of the issues and safeguard the software from malicious entities, Eaton recommends blocking Ports 4679 and 4680 at the enterprise network or home network where Intelligent Power Manager software is installed and used.
For additional information please see the Eaton Vulnerability Advisory.
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.