1. EXECUTIVE SUMMARY
- CVSS v3 9.0
- ATTENTION: Exploitable remotely/low skill level to exploit.
- Vendor: VISAM
- Equipment: VBASE
- Vulnerabilities: Relative Path Traversal, Incorrect Default Permissions, Inadequate Encryption Strength, Insecure Storage of Sensitive Information, Stack-based Buffer Overflow
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to read the contents of unexpected files, escalate privileges to system level, execute arbitrary code on the targeted system, bypass security mechanisms, and discover the cryptographic key for the web login.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of VBASE, an automation platform, are affected:
- VBASE Editor, Version 188.8.131.52
- VBASE Web-Remote Module
3.2 VULNERABILITY OVERVIEW
Input passed in the URL is not properly verified before use, which may allow an attacker to read arbitrary files from local resources.
Weak or insecure permissions on the VBASE directory may result in elevation of privileges or malicious effects on the system the next time a privileged user runs the application.
Weak hashing algorithm and insecure permissions may allow a local attacker to bypass the password-protected mechanism through brute-force attacks, cracking techniques, or overwriting the password hash.
An unauthenticated attacker may discover the cryptographic key from the web server and gain information about the login and the encryption/decryption mechanism, which may be exploited to bypass authentication of the HTML5 HMI web interface.
A vulnerable ActiveX component may be exploited resulting in a buffer overflow, which may allow remote attackers to cause a denial-of-service condition and execute arbitrary code.
- CRITICAL INFRASTRUCTURE SECTORS: Multiple
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Gjoko Krstic of Applied Risk reported these vulnerabilities to CISA.
VISAM has not yet responded to provide mitigations for these vulnerabilities.
For more information about these vulnerabilities and how VISAM plans to address them, please contact VISAM using the information provided on their contact page (German language).
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
CISA also recommends users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
No known public exploits specifically target these vulnerabilities.
Toll Free: 1-888-282-0870