All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 8.8
- ATTENTION: Exploitable from adjacent network/low skill level to exploit
- Vendor: ABB
- Equipment: CP635 HMI
- Vulnerability: Use of Hard-coded Credentials
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker to prevent legitimate access to an affected system node, remotely cause an affected system node to stop, take control of an affected system node, or insert and run arbitrary code in an affected system node.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
ABB reports the vulnerability affects the following CP635 HMI products:
- CP620, order code: 1SAP520100R0001, revision index G1 with BSP UN31 v1.76 and prior
- CP620, order code: 1SAP520100R4001, revision index G1 with BSP UN31 v1.76 and prior
- CP620-WEB, order code: 1SAP520200R0001, revision index G1 with BSP UN31 v1.76 and prior
- CP630, order code: 1SAP530100R0001, revision index G1 with BSP UN31 v1.76 and prior
- CP630-WEB, order code: 1SAP530200R0001, revision index G1 with BSP UN31 v1.76 and prior
- CP635, order code: 1SAP535100R0001, revision index G1 with BSP UN31 v1.76 and prior
- CP635, order code: 1SAP535100R5001, revision index G1 with BSP UN31 v1.76 and prior
- CP635-B, order code: 1SAP535100R2001, revision index G1 with BSP UN31 v1.76 and prior
- CP635-WEB, order code: 1SAP535200R0001, revision index G1 with BSP UN31 v1.76 and prior
3.2 VULNERABILITY OVERVIEW
The ABB CP635 HMI component implements hidden administrative accounts used during the provisioning phase of the HMI interface.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Switzerland
ABB reported this vulnerability to NCCIC.
ABB recommends users apply the BSP update on affected CP600 control panels at their earliest convenience.
- New version of PB610 Panel Builder 600 v126.96.36.1994, which is provided via Automation Builder 2.2 SP2.
- New version of BSP (board support package) UN31 v2.31.
Please see ABB cybersecurity advisory document number 3ADR010376 for more information about this vulnerability, and two other security issues and their mitigations.
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as virtual private networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
- Only use software from trusted sources.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.