All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Advantech
- Equipment: WebAccess
- Vulnerabilities: Stack-based Buffer Overflow, External Control of File Name or Path, Improper Privilege Management, Path Traversal
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to execute arbitrary code, access files and perform actions at a privileged level, or delete files on the system.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of WebAccess are affected:
- WebAccess Versions 8.3.1 and prior.
3.2 VULNERABILITY OVERVIEW
Several stack-based buffer overflow vulnerabilities have been identified, which may allow an attacker to execute arbitrary code.
A .dll component is susceptible to external control of file name or path vulnerability, which may allow an arbitrary file deletion when processing.
An improper privilege management vulnerability has been identified, which may allow an attacker to access those files and perform actions at a system administrator level.
A path traversal vulnerability may allow an attacker to execute arbitrary code.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing, Energy, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: East Asia, United States, and Europe
- COMPANY HEADQUARTERS LOCATION: Taiwan
Mat Powell of Trend Micro Zero Day Initiative working with Trend Micro’s Zero Day Initiative reported these vulnerabilities to NCCIC.
Advantech has released Version 8.3.3 of WebAccess to address the reported vulnerabilities. Users can download the latest version of WebAccess at the following location:
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.