All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 8.8
- ATTENTION: Low skill level to exploit
- Vendor: Rockwell Automation
- Equipment: RSLinx Classic and FactoryTalk Linx Gateway
- Vulnerability: Unquoted Search Path or Element
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an authorized, but non-privileged local user to execute arbitrary code and allow a threat actor to escalate user privileges on the affected workstation.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of RSLinx Classic, a software platform that allows Logix5000 Programmable Automation Controllers to connect to a wide variety of Rockwell Software applications, and FactoryTalk Linx Gateway, software that provides an Open Platform Communications (OPC) Unified Architecture (UA) server interface to allow the delivery of information from Rockwell Software applications to Allen-Bradley controllers, are affected:
- RSLinx Classic Versions 3.90.01 and prior, and
- FactoryTalk Linx Gateway Versions 3.90.00 and prior.
3.2 VULNERABILITY OVERVIEW
An unquoted search path or element may allow an authorized, but non-privileged local user to execute arbitrary code and allow a threat actor to escalate user privileges on the affected workstation.
- CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing, Energy, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Wisconsin, USA
Gjoko Krstic of Zero Science Lab reported this vulnerability to Rockwell Automation, and Rockwell Automation reported it to the NCCIC.
Rockwell Automation recommends all users update to the following RSLinx Classic and FactoryTalk Linx Gateway versions:
- RSLinx Classic Versions 3.90.01 and prior, update to v4.00.01 or later available at:
- FactoryTalk Linx Gateway Versions 3.90.00 and prior, update to FactoryTalk Linx Gateway v6.00.00 or later available at:
Rockwell also recommends the following mitigating procedures to those who are unable to upgrade to the latest version:
- Visit Knowledge Base Article ID 939382, which describes how to identify whether or not the service path contains spaces (i.e., is vulnerable); how to manually address this vulnerability through a registry edit; and describes the process of implementing these edits.
https://rockwellautomation.custhelp.com/app/answers/detail/a_id/939382 (login required).
- Run all software as a user, not as an administrator, to minimize the impact of malicious code on the infected system.
- Use Microsoft AppLocker or other similar whitelisting application to help mitigate risk. Information on using AppLocker with Rockwell Automation products is available at:
https://rockwellautomation.custhelp.com/app/answers/detail/a_id/546989 (login required).
- Ensure the least-privilege user principle is followed, and user/service account access to shared resources (such as a database) is only granted with a minimum amount of rights as needed.
For more information, please see Rockwell Automation’s knowledgebase advisory number 1073800 on this issue at the following location:
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability. This vulnerability is not exploitable remotely.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.