All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 5.3
- ATTENTION: Low skill level to exploit.
- Vendor: Omron
- Equipment: CX-One
- Vulnerabilities: Stack-based Buffer Overflow, Heap-based Buffer Overflow, Type Confusion.
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of CX-One are affected:
- CX-One Versions 4.42 and prior, including the following applications:
- CX-FLnet versions 1.00 and prior,
- CX-Protocol versions 1.992 and prior,
- CX-Programmer versions 9.65 and prior,
- CX-Server versions 5.0.22 and prior,
- Network Configurator versions 3.63 and prior, and
- Switch Box Utility versions 1.68 and prior.
3.2 VULNERABILITY OVERVIEW
Parsing malformed project files may cause a heap-based buffer overflow.
Parsing malformed project files may cause a stack-based buffer overflow.
Parsing malformed project files may allow the pointer to call an incorrect object resulting in an access of resource using incompatible type condition.
- Critical Infrastructure Sectors: Critical Manufacturing
- Countries/Areas Deployed: Worldwide
- Company Headquarters Location: Japan
Rgod, working with Trend Micro’s Zero Day Initiative, reported these vulnerabilities to NCCIC.
Omron has released an updated version of CX-One to address the reported vulnerabilities. These releases are available through the CX-One auto-update service.
- CX-FLnet version 1.10,
- CX-Protocol version 1.993,
- CX-Programmer versions 9.66,
- Common Module including CX-Server version 5.0.23,
- Network Configurator version 3.64, and
- Switch Box Utility version 1.69
NCCIC recommends that users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT website.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities. These vulnerabilities are not exploitable remotely.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.