All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
CVSS V3 10
ATTENTION: Remotely exploitable/low skill level to exploit.
Vendor: Carlo Gavazzi
Equipment: VMU-C EM, VMU-C PV
Vulnerabilities: Access Control Flaws, CSRF, Sensitive Information Stored In Clear Text
Carlo Gavazzi reports that the vulnerabilities affect the following versions:
- VMU-C EM prior to firmware Version A11_U05, and
- VMU-C PV prior to firmware Version A17
Successful exploitation of these vulnerabilities could allow the attacker to execute configuration parameter changes and saving modified configuration.
Carlo Gavazzi has created firmware updates that mitigate these vulnerabilities. Carlo Gavazzi recommends upgrading to the following firmware versions:
- VMU-C EM A11_U05 for VMUC EM, and
- VMU-C PV A17 for VMUC PV.
The relevant firmware versions are available either by means of the firmware update function embedded in the VMU-C or by downloading them from Carlo Gavazzi’s web site. Please open the link:
- Click on “Select the Product.”
- Choose “Web-Server” from the “FUNCTION” column.
- A list including both VMU-C EM and VMU-C PV will appear; select the target VMU-C model from the list.
- From the “downloads” section on the right, click on the “Software” icon to start downloading the updated firmware package.
NCCIC/ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability. Remotely exploitable. Low skill level is needed to exploit.
The access control flaw allows access to most application functions without authentication.
Successful exploitation of this vulnerability can allow execution of unauthorized actions on the device such as configuration parameter changes, and saving modified configuration.
Sensitive information stored in clear-text.
Karn Ganeshen has reported these vulnerabilities.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.