All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
Martin Jartelius of Outpost24 has identified a directory traversal vulnerability in Honeywell’s XL Web Controller. Honeywell has produced an update that mitigates this vulnerability.
This vulnerability could be exploited remotely.
The following XLWeb controller versions are affected:
- XL1000C50 EXCEL WEB 52 I/O,
- XL1000C100 EXCEL WEB 104 I/O,
- XL1000C500 EXCEL WEB 300 I/O,
- XL1000C1000 EXCEL WEB 600 I/O,
- XL1000C50U EXCEL WEB 52 I/O UUKL,
- XL1000C100U EXCEL WEB 104 I/O UUKL,
- XL1000C500U EXCEL WEB 300 I/O UUKL, and
- XL1000C1000U EXCEL WEB 600 I/O UUKL.
An attacker may use this vulnerability to generate a valid login for an administrative user on the Honeywell XLWeb controller giving the attacker full administrator access to the system. The XLWEB application effectively becomes an entry point into the network where it is located.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Honeywell is a US-based company that maintains offices worldwide.
The affected products, XLWeb controllers, are web-based SCADA systems. According to Honeywell, XLWeb controllers are deployed across several sectors including Critical Manufacturing, Energy, Water and Wastewater Systems, and others. Honeywell estimates that these products are used primarily in Europe and the Middle East.
By using a directory traversal vulnerability in the FTP server, it is possible to gain access to the web root directory.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
The update for this vulnerability is Excel Web Linux version 2.04.01 (March, 2014) or later plus the programing tool CARE version 10.02 (March 2014) or later. Customers are encouraged to contact their local Honeywell HBS branch to have their sites updated to the latest version.
In the Centraline partner channel, Excel Web controllers also have been sold under the brand name “FALCON.” Centraline partners can directly access http://www.centraline.com and get these versions.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
- a. CWE-22: Improper Limitation of a Pathname to a Restricted Directory ('Path Traversal'), http://cwe.mitre.org/data/definitions/22.html, web site last accessed March 17, 2015.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2015-0984, NIST uses this advisory to create the CVE web site report. This web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:C/I:C/A:C, web site last accessed March 17, 2015.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.