All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
Reid Wightman of Digital Bond has identified an authentication vulnerability in Phoenix Contact Software’s ProConOs and MultiProg applications. KW-Software originally wrote these applications without authentication intentionally.
This vulnerability could be exploited remotely.
The following applications are affected:
- ProConOs all versions, and
- MultiProg all versions.
An exploitation of this vulnerability could allow any network user to interact with the process control and change the ladder logic.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Phoenix Contact Software is a German-based automation software company. Prior to January 2015, they were known as KW-Software GmbH. Phoenix Contact Software provides software solutions to vendor companies. These vendor companies offer products integrated with Phoenix Contact Software worldwide.
These applications allow users to run process control and manage IEC 61131 logic.
The protocol behind the application software does not have an authentication mechanism. This allows anyone with network access to inject commands to the protocol.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
Phoenix Contact Software designed the applications and protocols without authentication mechanisms. It is the understanding of Phoenix Contact Software that vendors using the application software and its protocol would incorporate its own authentication mechanism in its final product. Phoenix Contact Software is considering adding authentication software into future versions of its application software and its protocol.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. CWE-306: Missing Authentication for Critical Function, http://cwe.mitre.org/data/definitions/306.html, web site last accessed January 13, 2014.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2014-9195, NIST uses this advisory to create the CVE web site report. This web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:C/I:C/A:C, web site last accessed January 13, 2014.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.