All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
NCCIC/ICS-CERT received a report from the Zero Day Initiativea (ZDI) regarding a project directory information disclosure vulnerability in the Ecava Sdn Bhd IntegraXor application. This vulnerability was reported to ZDI by security researcher “Alphazorx aka technically.screwed.” Ecava Sdn Bhd has produced an update that mitigates this vulnerability.
This vulnerability could be exploited remotely.
The following Ecava Sdn Bhd IntegraXor versions are affected:
- Ecava Sdn Bhd IntegraXor - 4.1.4360 and earlier.
An attacker can use a crafted URL to download certain files in the project directory, thus compromising the confidentiality of the system.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Ecava Sdn Bhd is a Malaysia-based software development company that provides the IntegraXor SCADA product. Ecava Sdn Bhd specializes in factory and process automation solutions.
The affected product, IntegraXor, is a suite of tools used to create and run a Web-based human‑machine interface for a SCADA system. IntegraXor is currently used in several areas of process control in 38 countries with the largest installation based in the United Kingdom, United States, Australia, Poland, Canada, and Estonia.
UNAUTHORIZED FILE ACCESSb
IntegraXor does not properly restrict access to files in the project directory. An attacker may use a specially crafted URL to download project backup files from the system project directory without any authentication.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
Ecava Sdn Bhd has issued a customer notification that details this vulnerability and provides mitigations to its customers. Ecava Sdn Bhd recommends users download and install the update, IntegraXor SCADA Server 4.1.4369, from their support Web site:
For additional information, please see Ecava’s vulnerability note:
NCCIC/ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
NCCIC/ICS-CERT also provides a section for control systems security recommended practices on the NCCIC/ICS-CERT Web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. NCCIC/ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the NCCIC/ICS-CERT Technical Information Paper, ICS-TIP-12-146-01B—Targeted Cyber Intrusion Mitigation Strategies,e that is available for download from the NCCIC/ICS-CERT Web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC/ICS-CERT for tracking and correlation against other incidents.
- aEcava IntegraXor Project Directory Information Disclosure Vulnerability, http://www.zerodayinitiative.com/advisories/ZDI-13-277/, Web site last accessed January 08, 2014.
- bCWE-529: Exposure of Access Control List Files to an Unauthorized Control Sphere, http://cwe.mitre.org/data/definitions/529.html, Web site last accessed January 08, 2014.
- cNVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2014-0752, NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- dCVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:P/I:P/A:P, Web site last accessed January 08, 2014.
- eTargeted Cyber Intrusion Detection and Mitigation Strategies, http://ics-cert.us-cert.gov/tips/ICS-TIP-12-146-01B, Web site last accessed January 08, 2014.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.