All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
This advisory was originally posted to the US-CERT secure Portal library on June 19, 2013, and is now being released to the ICS-CERT-Web page.
Independent researchers ZombiE and amisto0x07 have identified an improper input validation vulnerability in the GE CIMPLICITY WebView application. GE has produced an update that mitigates this vulnerability.
GE has released a security advisory (GEIP13-03) available on the GE Intelligent Platforms support Web site to inform customers about this vulnerability.
This vulnerability could be exploited remotely.
The following GE CIMPLICITY versions are affected:
- Proficy HMI/SCADA – CIMPLICITY: Version 4.01 to 8.2, and
- Proficy Process Systems with CIMPLICITY.
If the vulnerability is exploited, it could allow an unauthenticated remote attacker to cause the CIMPLICITY WebView and/or CIMPLITY built-in Web server to crash, or to run arbitrary commands on a server running the affected software, or could potentially allow an attacker to take control of the CIMPLICITY server.
An attacker can exploit the vulnerability by sending malicious messages over a TCP connection to the listening service. The attacks do not require authentication and can be conducted remotely. The vulnerable components are not enabled by default.
Impact to individual organizations depends on many factors that are unique to each organization. ICS‑CERT recommends that organizations evaluate the impact of these vulnerabilities based on their operational environment, architecture, and product implementation.
According to GE, Proficy HMI/SCADA–CIMPLICITY is a Client/Server-based human-machine interface/supervisory control and data acquisition (HMI/SCADA) application, which is deployed across multiple industries.
IMPROPER INPUT VALIDATIONa
The CimWebServer does not properly validate inputted information. By sending a specially crafted packet, an attacker could crash the WebView or built-in Web server, run arbitrary commands on a server running the affected software, or take control of the server. The vulnerable CIMPLICITY built-in Web server component is not enabled by default.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a medium skill would be able to exploit this vulnerability.
GE has released the following product updates that resolve this vulnerability:
- Proficy HMI/SCADA – CIMPLICITY 8.2 SIM 19
- Proficy HMI/SCADA – CIMPLICITY 8.1 SIM 25
- Proficy HMI/SCADA – CIMPLICITY 8.0 SIM 27
All the updates can be found at:
ICS‑CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategiesd ICS‑CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B—Targeted Cyber Intrusion Detection and Mitigation Strategiese , that is available for download from the ICS-CERT Web page (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS‑CERT for tracking and correlation against other incidents.
- aCWE-20: Improper Input Validation, http://cwe.mitre.org/data/definitions/20.html, Web site last accessed July 30, 2013.
- bNVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2013-2785, NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- cCVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:M/Au:N/C:N/I:C/A:C, Web site last accessed July 30, 2013.
- dCSSP Recommended Practices, http://ics-cert.us-cert.gov/content/recommended-practices, Web site last accessed July 30, 2013.
- eTargeted Cyber Intrusion Detection and Mitigation Strategies, http://ics-cert.us-cert.gov/tips/ICS-TIP-12-146-01B, Web site last accessed July 30, 2013.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.