All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
This advisory provides mitigation details provided by Siemens for a vulnerability that impacts the Siemens S7-1200 Web Application Module.
Siemens has reporteda a cross-site scripting (XSS) vulnerability in Siemens’s S7-1200 Programmable Logic Controllers (PLCs). Positive Technologiesb discovered this vulnerability and reported it directly to Siemens. Siemens has provided mitigations and a firmware update to fix this vulnerability.
Exploitation of this vulnerability would allow an attacker to partially modify application data and limit the availability of the device. This vulnerability affects the electric, critical manufacturing, chemical, and food and beverage sectors.
This vulnerability can be exploited remotely.
Siemens reports that the vulnerabilities affect the following versions of S7-1200 PLCs:
- V3.0.0, and
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of these vulnerabilities based on their operational environment, architecture, and product implementation.
Products in the Siemens SIMATIC S7-1200 PLC family have been designed for process control in industrial environments such as manufacturing, power generation and distribution, food and beverages, and chemical industries worldwide.
This vulnerability could be exploited remotely.
Existence of Exploit
No known public exploits specifically target this vulnerability.
An attacker with medium skill level would be able to exploit this vulnerability.
Siemens has released a security advisoryf that details this vulnerability. It recommends users obtain the new updated firmware for Versions 3.0.0 and 3.0.1 of the S7-1200 by contacting Technical Support in their region:
- Germany: +49 (0) 911 895 7222
- Americas: +1 423 262 5710
- Asia-Pacific: +86 10 6475 7575
Siemens also advises users who are unable to apply this firmware update to use the following mitigations.
- Utilize a modern Web browser with integrated XSS filtering mechanisms.
- Deactivate the S7-1200 Web server wherever possible.
For this version of firmware (3.0.2), Siemens has also removed the HTTP PUT functionality, because it is not used by the S7-1200 Web server.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the US-CERT Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategiesg. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS-CERT Technical Information Paper, ICS-TIP-12-146-01A—Cyber Intrusion Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
In addition, ICS-CERT recommends that users take the following measures to protect themselves from social engineering attacks.
- Do not click Web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
- a. SSA-279823, http://www.siemens.com/corporate-technology/en/research-areas/siemens-cert-security-advisories.htm, Web site last accessed October 9, 2012.
- b. Positive Technologies, http://ptsecurity.com/, Web site last accessed October 9, 2012.
- c. CWE-79: Improper Neutralization of Input During Web Page Generation, http://cwe.mitre.org/data/definitions/79.html, Web site last accessed October 9, 2012.
- d. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2012-3040 , NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- e. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:M/Au:N/C:P/I:P/A:C, Web site last accessed October 9, 2012.
- f. Siemens Security Advisory, http://www.siemens.com/corporate- technology/pool/de/forschungsfelder/siemens_security_advisory_ssa-279823.pdf, Website last accessed October 9, 2012.
- g. CSSP Recommended Practices, http://www.us-cert.gov/control_systems/practices/Recommended_Practices.html, Web site last accessed October 9, 2012.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.