All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
Researcher Daiki Fukumori of Cyber Defense Institute has identified a directory traversal vulnerability in Fultek’s WinTr SCADA application. Fultek was unable to validate this vulnerability and has not offered any mitigation plans.
ICS-CERT has validated the vulnerability. This vulnerability could be exploited remotely.
The following product is affected:
- WinTr Scada 4.0.5 and earlier.
Successful exploitation of this vulnerability may result in information leakage.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Fultek is a company based in Turkey. The affected product, WinTr Scada, is a Web-based SCADA system.
RELATIVE PATH TRAVERSALa
The WinTr Web server does not sanitize user input. By sending a specially crafted request to the Web server, an attacker may retrieve arbitrary files.
This vulnerability could be exploited remotely.
Existence of Exploit
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
The vendor has not offered any mitigation plans.
According to MITRE, the best mitigation for this type of vulnerability is to properly sanitize user input. MITRE also recommends, when the application is controlled by a third party and the code cannot be fixed, an application firewall may be used to validate input and mitigate the vulnerability. Running the application in a sandbox environment may also limit the scope of a compromise.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS-CERT Technical Information Paper, ICS-TIP-12-146-01A—Cyber Intrusion Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- aCWE, http://cwe.mitre.org/data/definitions/23.html, CWE-23: Relative Path Traversal, Web site last accessed September 18, 2012.
- bNVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2012-3011, NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.