All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
This advisory updates the ICS-CERT Alert titled “ICS-ALERT-12-097-01 - WAGO IPC Vulnerabilities” that was posted on the ICS-CERT Web site on April 06, 2012. This alert detailed a vulnerability report of “hard-coded” credentials and improper access controls in the WAGO I/O System 758 product line.
Researcher Reid Wightman of Digital Bond released these vulnerabilities without coordination with ICS-CERT or WAGO. After coordination with the researcher and the vendor, ICS-CERT determined that the improper authentication vulnerability is found in a third-party component used in multiple WAGO products. ICS-CERT is also coordinating this vulnerability with 3-S Smart Software Solutions, the third-party supplier. ICS-CERT will update an advisory with additional information from 3S as it becomes available.
WAGO has confirmed that its I/O System 758 products are configured with default operating system credentials. These credentials are disclosed, but WAGO provided no information on how to change the default passwords. WAGO has released a procedure with additional documentation on how to change the default operating system passwords in Models 758-874, 758-875, and 758-876. WAGO has also released a best security practices document that makes recommendations to its customers on how to best secure its industrial control system (ICS) products.
These vulnerabilities are exploitable remotely and proof-of-concept (PoC) exploits are known to exist.
The following WAGO products are affected:
- I/O System 758, Model 758-870,
- I/O System 758, Model 758-874,
- I/O System 758, Model 758-875, and
- I/O System 758, Model 758-876.
Attackers are able to exploit these vulnerabilities by using the default credentials to gain unauthorized administrative access to the systems.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of these vulnerabilities based on their operational environment, architecture, and product implementation.
According to WAGO’s Web site, WAGO is an international company based in Germany. They operate production facilities in Germany, Switzerland, Poland, China, and India. WAGO maintains offices worldwide.
According to WAGO, its products are deployed across several sectors including manufacturing, building automation, electric generation, transportation, and others. WAGO estimates that these products are used worldwide.
Use of Hard-Coded Passworda
The operating system software of the WAGO I/O System 758 product line uses three user accounts with default passwords and no method to change these passwords. An attacker could use the default password to gain administrative control through the Telnet service of the system
leading to a loss of integrity, loss of confidentiality, or loss of availability.
WAGO IPCs offer the 3-S Smart Software Solutions CoDeSys runtime to program the IPC similar to a programmable logic controller. The CoDeSys software allows unauthenticated connections to the server to run arbitrary commands. This could allow possible remote code execution. A separate advisory with a CVE number and CVSS score will be published by ICS-CERT for this vulnerability as more information becomes available.
These vulnerabilities could be remotely exploited.
Existence of Exploit
Public exploits are known to target these vulnerabilities.
An attacker with a low skill level would be able to exploit these vulnerabilities.
WAGO has developed a procedure for the I/O System 758, Models 758-874, 758-875, and 758-876 that allows users to change passwords for their default operating system accounts. The WAGO Security Settings Application Note discusses changing the Web-based Management passwords as well as the Linux console passwords and list security recommendations for their customers. This procedure does not provide instructions to change the default passwords on the I/O System 758, Model 758-870 as it is no longer being produced. WAGO has released a cybersecurity notification to its customers that details the best security settings and practices for its ICS products.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
The Control Systems Security Program (CSSP) also provides a section for control systems security recommended practices on the CSSP Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.