All information products included in https://us-cert.cisa.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://us-cert.cisa.gov/tlp/.
ICS-CERT has received a report from Michael Orlando of CERT Coordination Center (CERT/CC) identifying a vulnerability in Rockwell Automation Electronic Data Sheet (EDS) Hardware Installation Tool. This tool is bundled with RSLinx Classic for normal distribution. The install tool exhibits a buffer overflow vulnerability when parsing improperly formatted EDS files. This vulnerability is likely exploitable and could allow remote code execution, though that would require significant user interaction. Rockwell Automation has released a patch that has been verified by CERT/CC.
EDS Hardware Installation Tool Version 220.127.116.11 and all earlier versions are affected.
An attacker could exploit the vulnerability by tricking a user into opening a specially crafted EDS file, causing the EDS Hardware Installation Tool to crash, which would lead to possible execution of arbitrary code.
ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their environment, architecture, and product implementation. Critical infrastructure organizations are encouraged to use the information contained in this advisory to strengthen network defense and examine their own networks for possible compromise.
Rockwell Automation provides industrial automation control and information products worldwide, across a wide range of industries. RSLinx provides connectivity to plant floor devices for Rockwell software applications. To register a device on the network, product-specific information must be supplied via an EDS file. The RSLinx Hardware Installation Tool parses the EDS file containing the hardware’s specifications.
An attacker that alters a required EDS file and then uses it in the EDS Hardware Installation Tool could cause the tool to crash, allowing execution of arbitrary code. The subsequent stack-based buffer overflow1 usually results from an excessively recursive function call and is usually outside the scope of a program’s implicit security policy. When the consequence is arbitrary code execution, this can often be used to subvert any other security service.
This vulnerability is likely exploitable; however, it is not possible without user interaction. An attacker cannot initiate the exploit from a remote machine. The exploit is only triggered when a local user runs the vulnerable application and loads the malformed EDS file.
Existence of Exploit
No known exploits specifically target this vulnerability.
Crafting a working exploit for this vulnerability would be difficult. Social engineering is required to convince the user to accept the malformed EDS file. Additional user interaction is needed to load the malformed file. This decreases the likelihood of a successful exploit.
Rockwell Automation recommends concerned customers take the following immediate steps to mitigate risk associated with this vulnerability.
- Restrict physical access to the computer
- Establish policies and procedures such that only authorized individuals have administrative rights on the computer
- Obtain product EDS files from trusted sources (e.g., product vendor)
- Download and apply the Rockwell Automation issued Patch Aid 276774, available from the Rockwell Automation Support Center (requires an account logon for access): http://rockwellautomation.custhelp.com/app/answers/detail/a_id/276774.
ICS-CERT encourages asset owners to minimize network exposure for all control system devices. Critical devices should not directly face the Internet. Locate control system networks and remote devices behind firewalls and isolate them from the business network. When remote access is required, use secure methods such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a section for control system security recommended practices on the CSSP web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
In addition, ICS-CERT recommends that users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in e-mail messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding e-mail scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
- 1Mitre, http://cwe.mitre.org/data/definitions/121.html, website last visited June 09, 2011
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
Please share your thoughts.
We recently updated our anonymous product survey; we'd welcome your feedback.